EICR Report notes the following issues.
C2 - No RCD protection for socket-outlets for internal use BS7671
C2 - All lighting circuits need additional RCD protection
C2 - Cooker needs RCD protection
C3 - Consumer unit does not comply with current BS7671 standards
C3 - Basic insulation is visible outside fuse board
C3 - Socket is not working in kitchen
C3 - Water heater is not RCD protected
In summary most of these will be solved by an updated consumer unit, and I will be needing either a new EICR or a "minor works report" to put with the original.
See attached photos of the consumer unit and of the EICR report (highlighted issues in yellow).
Excellent work, really knows his stuff and great communication with quick responses which is a rarity. Everything was clear from the outset, and he did his best to explain a difficult problem and the best possible solution, always arrived on time ... and job done !!!